Over 698,000 strictly plumbing related posts
Plumbing education, information, advice, help and suggestions are provided by some of the most experienced plumbers who wish to "give back" to society. Since 1996 we have been the best online (strictly) PLUMBING advice site. If you have questions about plumbing, toilets, sinks, faucets, drains, sewers, water filters, venting, water heating, showers, pumps, and other strictly PLUMBING related issues then you've come to the right place. Please refrain from asking or discussing legal questions, or pricing, or where to purchase products, or any business issues, or for contractor referrals, or any other questions or issues not specifically related to plumbing. Keep all posts positive and absolutely no advertising. Our site is completely free, without ads or pop-ups and we don't tract you. We absolutely do not sell your personal information. We are made possible by:
I'm trying to figure what the cause is but here's what's happening. When I shower in the upstairs bathroom, the toilet downstairs starts to leak from the base. I checked the water level on the toilet bowl and it seems normal and so I'm pretty sure it's coming from the base. I looked around online and read that this could be from having an old wax ring on the toilet?
But also, the carpet area on the bathroom entrance is wet as well now. It seems like its coming from underneath the floor? Most likely the pipe?
I'll include the image of it below:
Not sure if this is something I can fix on my own or need to call a plumber. Would be great to get some advice on how I can solve this issue. Thank you!
Edited 2 times.
There is a partial stoppage in the piping downstream of the toilet.
The water is backing up and seeping out through the wax seal which is NOT a pressure tight seal.
If there is no CO in the downstream piping the toilet will need to be pulled and the line snaked through the flange opening.
As the wax seal needs replacing ANYWAY ......................
"Measure Twice & Cut Once" - Retired U.A. Local 1 & 638
yeah, as my friend fro0m SC says.. you have a partial stoppage.
the fact that the rug is wet means there is another leak besides the toilet seal.
the stoppage is in a bigger pipe which means a small homeowner snake will not clear it.
probably should call a plumber to clear the stoppage, address the leak under the rug and reset the toilet.
- Inappropriate messages or blatant advertising will be deleted. We cannot be held responsible for bad or inadequate advice.
- Plbg.com has no control over external content that may be linked to from messages posted here. Please follow external links with caution.
- Plbg.com is strictly for the exchange of plumbing related advice and NOT to ask about pricing/costs, nor where to find a product (try Google), nor how to operate or promote a business, nor for ethics (law) and the like questions.
- Plbg.com is also not a place to ask radiant heating (try HeatingHelp.com), electrical or even general construction type questions. We are exclusively for plumbing questions.
Search for plumbing parts on our sponsor's site:
Special thanks to our sponsor: