Over 698,000 strictly plumbing related posts
Plumbing education, information, advice, help and suggestions are provided by some of the most experienced plumbers who wish to "give back" to society. Since 1996 we have been the best online (strictly) PLUMBING advice site. If you have questions about plumbing, toilets, sinks, faucets, drains, sewers, water filters, venting, water heating, showers, pumps, and other strictly PLUMBING related issues then you've come to the right place. Please refrain from asking or discussing legal questions, or pricing, or where to purchase products, or any business issues, or for contractor referrals, or any other questions or issues not specifically related to plumbing. Keep all posts positive and absolutely no advertising. Our site is completely free, without ads or pop-ups and we don't tract you. We absolutely do not sell your personal information. We are made possible by:
My hot water heater discharged. Found that the upper element went bad so for my good sense knowing everything was good replaced both heating elements and thermostats and set to a low setting for hot water. After all that was done let it heat up again and discharged once again so i replaced the relief valve. After all i have done it once again discharged and not sure where to go next and have been taking cold showers since even in this below freezing weather.
Any thoughts or further suggestions will be greatly appreciated!!
What is the actual hot water temperature when the T-P valve discharges?
Do you have an expansion tank?
If so, check it for air pressure and / or 'waterlogging'.
If not you may need to install one.
"Measure Twice & Cut Once" - Retired U.A. Local 1 & 638
o about actually TESTING the system to see that it is working correctly, instead of just willy nilly replacing things. There are two different types of upper thermostats and if you get the wrong one and wire it like the old one it will NEVER turn off the upper element until it trips the high limit switch.
- Inappropriate messages or blatant advertising will be deleted. We cannot be held responsible for bad or inadequate advice.
- Plbg.com has no control over external content that may be linked to from messages posted here. Please follow external links with caution.
- Plbg.com is strictly for the exchange of plumbing related advice and NOT to ask about pricing/costs, nor where to find a product (try Google), nor how to operate or promote a business, nor for ethics (law) and the like questions.
- Plbg.com is also not a place to ask radiant heating (try HeatingHelp.com), electrical or even general construction type questions. We are exclusively for plumbing questions.
Search for plumbing parts on our sponsor's site:
Special thanks to our sponsor: