Over 692,000 strictly plumbing related posts
Plumbing advice, answers, information, help and suggestions are provided here by experienced plumbers who wish to "give back" to others. Since 1996 we have been the best online (strictly) PLUMBING forum. If you have questions and are looking for answers or wish to discuss anything about toilets, sinks, faucets, drainage, water filters, venting, water heating, showers, pumps, and other exclusively PLUMBING related issues then you've come to the right place. Please refrain from asking or discussing legal questions, or pricing, or where to purchase products, or any business issues, or for contractor referrals, or any other questions or issues not specifically related to plumbing. Keep all posts positive and absolutely no advertising. Our site is completely free, without ads or pop-ups and we don't tract you. We absolutely do not sell your personal information. We are made possible by:
There is some work to be done at a farm milk parlor setting replacing few faucets. The hot water is around 180 degrees for sanitation purposes, and around 70 psi. Currently all pex with brass (non viega) fittings with stainless side pinch crimp clamps.
My question is, will my viega pureflow press fittings with attached sleeves work under that high temp or not?
I also want to install the viega pureflow press ball valves w/attached sleeves on 2 faucets. Obviously, cold side will be fine,
but will the 1/4 turn ball valves take the 180 degree water without internal leaking?
I don't want problems with the valves leaking and or fittings blown due to high temperature.
Thank you for any advice!
Edited 2 times.
? Operating Temperature: 180°F max (potable)
200°F max (hydronic)
? Operating Pressure: 160 psi max at 73°
100 psi max at 180°F
? Test Pressure: Recommended: 100 psi, Maximum: 160 psi
Edited 2 times.
- Inappropriate messages or blatant advertising will be deleted. We cannot be held responsible for bad or inadequate advice.
- Plbg.com has no control over external content that may be linked to from messages posted here. Please follow external links with caution.
- Plbg.com is strictly for the exchange of plumbing related advice and NOT to ask about pricing/costs, nor where to find a product (try Google), nor how to operate or promote a business, nor for ethics (law) and the like questions.
- Plbg.com is also not a place to ask radiant heating (try HeatingHelp.com), electrical or even general construction type questions. We are exclusively for plumbing questions.
Search for plumbing parts on our sponsor's site:
Special thanks to our sponsor: